Magnum Inspections Inc.
Serving South Florida Since 1994 Martin County: (772) 214-9929 Broward/Palm Beach Counties: (954) 340-6615
Email me at: email@example.com
This page will tell you about GFCI (Ground Fault Interrupter Circuit) protection. G.F.I.s and G.F.C.I.s are Ground fault interrupter and Ground fault circuit interrupters. The ground fault interrupter is a receptacle that has the ability to open or disconnect the power from the output of the receptacle. The ground fault circuit interrupter is a breaker that has the ability to disconnect the power from a circuit.
The ground fault senses a difference in the flow of current from the hot wire through the neutral, if that difference is about 5 milliamps or more the ground fault will trip the circuit out. It actually assumes that if the current is not flowing in the neutral it is flowing through something else. Some motor windings have sufficient losses to cause one to trip out so don't use a G.F.I. circuit for a refrigerator or washer outlet.
You should use (and the NEC requires) the use of G.F.I. protected outlets within6 feet of a sink, anywhere in a bathroom, in a garage or outside; anywhere an outlet can be reached from a water source, a wet area, or earth ground, you should use G.F.I. protection.
A G.F.I. receptacle has a line side (incoming power) and a load side (outgoing power).
The receptacle will not work if the incoming power is connected to the load side of the receptacle. Connect the incoming power to the line marked terminals and the continuation of the circuit (the next outlet) to the load terminals. The one G.F.I. will protect all the following plugs or receptacles connected in this way. Even if you don't have a continuation of the circuit, connect the power to the line side of the receptacle.
G.F.I. receptacles and G.F.C.I. breakers have a test button that should cause the circuit to trip, operate the test button after installing and regularly there after to be sure it works properly.
Where do you put G.F.I.s?
The are two types of G.F.C.I.s
in homes, the G.F.C.I outlet and the G.F.C.I circuit breaker. Both do the same
job, but each has different applications and limitations.
It protects any appliance plugged into it, and can also be wired to protect other outlets that are connected to it. In reality, G.F.I. protection is designed to protect persons and as a result, items plugged into those outlets are also protected.
The G.F.C.I. circuit breaker
controls an entire circuit, and is installed as a replacement for a circuit
breaker on your home's main circuit board. Rather than install multiple G.F.C.I.
outlets, one G.F.C.I. circuit breaker can protect the entire circuit. There is a
test button and a reset button on these units. If you press the test button the
reset should pop out. To reset, just push the reset button in.
It is not a good idea to put lights on G.F.C.I. protected circuits so you aren't left in the dark if the circuit trips. Generally, equipment such as refrigerators, freezers and sump pumps that cannot go without electrical power for an extended period of time without causing costly losses or property damage should not be placed on a G.F.C.I. protected circuit. G.F.C.I.s are very sensitive and are subject to nuisance tripping. G.F.C.I. receptacles don't last outdoors even under the best of conditions. Be sure to test the device using the "test" button before you use one.
Can you use a G.F.I. in an ungrounded outlet?
Click on the link below for a chart that will tell you when each requirement for G.F.I. protection was added to the electric code courtesy of Jerry Peck and the late Norm Sage.
Check with your local code official to be sure what code you are operating under.
Click on the links to the left for more important information.
Martin County: (772) 214-9929 Broward/Palm Beach Counties: (954) 340-6615
Email me at: firstname.lastname@example.org
Copyright Magnum Inspections Inc. 1994-2018--All Rights Reserved